Basic PDU - 3.6kW, CB-26V0AE01F6
Branch Circuit ProtectionThis PDU meets the UL and IEC 60950-1 requirement for branch circuit protection through use of UL489 rated magnetic-hydraulic circuit breakers or UL248 fuses.
High Retention Locking OutletsReceptacles have high retention and are compatible with P-Lock type power cords.
Flexible MountingIncludes standard button mounts along with provisions for custom mounting brackets (contact Server Technology for details).
DescriptionThe Server Technology® Basic PDU provides reliable power distribution for installing IT equipment into the rack/cabinet.
|Input Voltage (V):||208|
|Input Plug:||IEC C20 100-240V Inlet|
|Input Current (A):||20|
|Input Current Rated (A):||16|
|Input Power Capacity (kW):||3.6|
|Requires PTCORD-L1, -L2, -L3, -L4, -L5, -L6, or –L7|
|(24) x IEC 60320/C13||North American Rating: ≤ 12A @208V L-N (15A Peak)
Global Rating: ≤ 10A @230V L-N
|(2) x IEC 60320/C19||North American Rating: ≤ 16A @208V L-N (20A Peak)
Global Rating: ≤ 16A @230V L-N
Branch Circuit ProtectionUL489 Compliant 2-pole, 20A trip circuit breakers, two (2) branch, rating: ≤ 16A, 5 kAIC Interrupt Rating
PhysicalDimensions: 35.5in tall x 1.75in wide x 1.75in deep [902mm x 45mm x 45mm]
EnvironmentalOperating Environment: 32°F to 122°F / 0°C to 50°C | 8%RH to 90%RH non-condensing | 6,500ft/2km elevation
Storage Environment: -40°F to 185°F / -40°C to 85°C | 8%RH to 90%RH non-condensing | 50,000ft/15km elevation
Quiescent / Unloaded Power Draw: < 10W for all configurations
Communications & SecurityNot Applicable
cTUVus Mark to UL 60950-1:2007 R10.14
CAN/CSA-C22.2 No. 60950-1-07+A1:2011+A2:2014
FCC Part 15 Subpart B Sections 15.107 and 15.109, Class A
TUV T-Mark to EN 60950-1:2006+A11+A1+A12+A2
EMC to EN55024 (2010) and EN55032 (2012)
RoHS, European Hazardous Materials Directive (Recast) 2011/65/EU
Measurement AccuracyInput Measurement Accuracy:
LED Current = ± 10% at 0.1 amp (0.3 - 9.9 amps) and 1 amp (> 9.9 amps) resolution
GUI Current = ± 5% at 0.01 amp resolution (above 0.25 amp)